Medium Voltage STA Armoured Cable
xlpe insulated power cable
-> Usage of Medium Voltage STA Armoured Cable(medium voltage steel tape armoured cable):
Used for power transmission and distribution line with voltage rated at 35kV and below. In comparison with PVC Insulated Power Cable, xlpe power cable boasts not only characteristics of excellent electricity, mechanism, heat and aging-resistant, environment stress-resistant and chemical corrosion-resistant, but also simple structure, light weight, no restriction by laying drop, and high temperature allowance for long-term working.
-> Number of cores about Medium Voltage STA Armoured Cable(medium voltage steel tape armoured cable):
The core number can be one core, two core, three core, four core, five core, 3+1 core, 3+2 core, 4+1 core and so on.
-> XLPE insulation and PVC sheached steel tape armoured power cable technical parameter:
1. Rated voltage: Uo/U: 66kV, 26/35kV, 21/35kV, 12/20 kV (24 kV), 8.7/10kV, 8.7/15kV, 6/6kV, 6/10kV.
2. No. of core: Single-core, Three-core etc.
3. The highest allowed operating temperature of conductor for long-term working is 90°C. In short-circuit (Max. Long-term is no more than 5 seconds). The highest temperature for conductor is no more than 250°C.
4. D.C Resistance of the conductor complies with the stipulations of GB/T3956-1997.
5. The environment temperature should be no lower than 0 when lay. Otherwise it should be preheated.
6.The cable is laid without horizontal drop limit. The Min. Bending radius of three-core cable should be no smaller than 12 times of cable outer diameter.
7. Working Frequency Voltage Test:
For cable with Uo of 3.6kV or lower: 2.5Uo+2kV/5min without puncture.
For cable with Uo of 3.6kv~18kV: 3.5Uo/5min without puncture.
For cable with Uo of 21kV and 26 kV: 2.5Uo/30min without puncture.
Medium Voltage STA Armoured Cable(medium voltage steel tape armoured cable) ----------Performance Characteristics:
1) The long-term permissible operation temperature of conductor shall not be higher than 70°C.
2) Conductor Max. short circuit (not more than 5 seconds)temperature shall not be higher than 160°C.
3) The cable is not limited by drop in level when being laid,and the environment temperature shall not be 0°C.
4) Perfect chemical stability,resistant against acids,alkalis,grease and organic solvents,and flame retradance.
5) Light weight,perfect bending properties,installed and maintained easily and conveniently.